In the water treatment process, solid-liquid separation and its equipment are one of the key projects. Dissolved air flotation is one of the most effective methods whose specific gravity near than that of water.As a new type of air flotation equipment, GDXF Type DAF is an excellent sewage treatment technology removing grease, gelatinous substance and suspended matter easily.
Due to its unique features, GDXF can be applied in various domains with the advantages of simple design, easy operation and stable running.
二、Type and Its Indication
GDXF— □ —— Treatmentcapacity (m3/h)
※No air compressor and pressure vessel
※Save operating cost, floor space and investment
※Simple, compact and maintenance-free
GDXF Type dissolved air flotation is suitable for:
※Disposal of oily waste water treatment in petrochemical industry
※Oily waste water treatment and reinjection water in oil exploitation industry
※Disposal of slaughter waste water in meatpacking industry
※Grease and effluent treatment in dairy industry
※The treatment of effluents generated by the pulp and paper industries
※Oily waste water treatment in machinery processing industry
The performance of GDXF is mainly determined by the gas content in the multiphase mixture liquid. When pump inhales liquid, it forms negative pressure at the pump inlet where air is inhaled through suction hole and liquid. Then air is dissolved into water by high speed rotating pump impeller. By adjusting operating points and solid-liquid proportion, it can achieve massive dispersed micro-bubbles or meet maximum carrying capacity. Based on different pump specification, gas content in liquid can reach 30%. When this saturated water (over-saturated water) flows into dissolved air vessel, it can instantly release high-density micro-bubble whose average diameter is less than 30 through release device after a certain period of time.
Finally, flocculating sewage mixes up with these micro-bubble after entering into the flotation tank. Then these micro-bubbles attach to the suspended solids and float them to the surface. These suspended solids reply on the micro-bubbles to sustain the water surface, forming a floating layer on the surface of the unit. The floating layer is removed into scum tank by means of a skimming device.